Image may not reflect selected options.
Elkay EZH2O Bottle Filling Station with Integral SwirlFlo Fountain, Filtered Non-Refrigerated Stainless
Elkay EZH2O Bottle Filling Station with Integral SwirlFlo Fountain, Filtered Non-Refrigerated Stainless is rated out of 5 by 5.
|Number of Stations||2|
|Features||Antimicrobial, Filtered, Green Ticker, Hands Free, Laminar Flow, Real Drain, Visual Filter Monitor|
|Bubbler Style||Flexi-Guard ® Safety Bubbler|
|Mounting Option||Wall Mount (Inwall Frame/Plate)|
|Number of Stations Serving||2|
|Shipping Dimensions||L: 41-5/8"
|Approximate Shipping Weight (lbs)||121|
|Includes:||Fountain with Integral Bottle Filling Station (EDFPBM117WS-F), Mounting Frame (MFWS200), Filter|
|Made or Assembled USA||built|
|Code Compliance Drinking Water||ADA & ICC A117.1
ASME A112.19.3/CSA B45.4
Buy American Act
CAN/CSA C22.2 No. 120
NSF 372 (lead free)
|Special Note||Coming soon: Elkay’s ezH2O is getting a new look. The model you receive may have an updated logo, different from what is shown here.|
Rated 1 out of 5 by Don Wallace from Access panel needed for code compliance Installing this fountain in a government building; the instructions do not specify that an access panel is needed, but it is. The plumbing, and electrical code in MD require access to both the drain connections, and the outlet it plugs into, respectively. The instructions indicate an optional access panel, but provide no further information, i.e part number. It should be clearly indicated that access is required for installation, as there is no way to make final plumbing connections once the fountain is installed.
Date published: 2019-01-10
Rated 1 out of 5 by PaulB from Rear access not indicated but required? My plumbing contractor is telling me that they cannot install or service this drinking fountain without adding two access panels behind the drinking fountain. This is not indicated on any of the installation documents. If rear access is necessary the documents should clearly indicate same or provide more installation detail for accessing drain connections.
Date published: 2018-11-13
Rated 1 out of 5 by Plumber303 from Impossible to hook up without rear access The installation manual is incomplete and inadequate. Drain piping for the bottle filler is not addressed, there is no way to access the water filter. The submittal data shows an "optional" access panel that would mount below the unit but is unclear how that would rectify the issues with accessing any of the final connections.
Date published: 2019-01-23
Rated 1 out of 5 by teddy kgb from no piping diagram for finish install i have no idea how to set finish on this product, i've called and talked to two different engineers and they both told me that it's a hard install, that is all the both of them offered to me as far as help, if they know it's a difficult hook up why not find someone who has done it a take a picture and show it on their website, better yet a youtube video......it';s not like elkay is a cheap product.....i'm working at uci and clueless on what i'm going to do about this and i have 32yrs in the plumbing field
Date published: 2020-03-24
Rated 5 out of 5 by kmh2 from GPM for the drinking fountain? I see GPM for the fillable portion. need to know GPM for drinking portion for code review.
Date published: 2019-09-12
What is the minimum wall thickness required for this drinking fountain with the EWS 3000 Filter Kit?
Hello Marissa - The minimum wall depth for this model would be 8" for the drain connection and bottle filler electrical. Thank you for your question!
Date published: 2020-02-25
Can a water filter be added to this water fountain?
Hello John H - Yes, EWF3000 can be added to this unit to make it filtered. Thank you for your question!
Date published: 2020-02-13
Can a remote water chiller be added to this unit?
Hello Angela! Yes, the ECH8 will work with this unit. Thank you for your question!
Date published: 2019-06-14
Do you need a access panel located behind unit to install, as stated in the review.
Yes, if there is no access from behind; there will be no way to replace the filter. You will also not pass a plumbing, or electrical inspection in MD. They need to be more clear about that in their product literature.
Date published: 2019-01-11
after replacing the filter the change filter light is still red how can we get that to change?
Hello Robert - Please refer to the manual (http://www.elkay.com/wcsstore/lkdocs/care-cleaning-install-warranty-sheets/1000002503.pdf) for instructions. You will need to remove the set screw under the round cover plate on the back of the fountain arm. Underneath the round cover plate is where the reset button will be. Thank you for your question!
Date published: 2018-11-05
Is this model hard wired or plug connected?
Hello Rich - This unit is a non-refrigerated unit and the bottle filler is electronic and plug in. Thank you for your question!
Date published: 2018-11-05