Image may not reflect selected options.
Elkay EZH2O Bottle Filling Station, & Single High Efficiency Vandal-Resistant Cooler, Filtered Refrigerated Stainless
|Number of Stations||1|
|Features||Antimicrobial, Filtered, Green Ticker, Hands Free, High Efficiency, Laminar Flow, Real Drain, Vandal Resistant, Visual Filter Monitor|
|Bubbler Style||Vandal Resistant StreamSaver |
|Mounting Option||Wall Mount (On Wall)|
|Chilling Capacity||8.0 GPH|
|Number of Stations Serving||1|
|Shipping Dimensions||L: 24"
|Approximate Shipping Weight (lbs)||94 lbs.|
|Includes:||Water Cooler (LVRCGRN8WS), Bottle Filler (LZWSR), Filter|
|Made or Assembled USA||built|
|Code Compliance Drinking Water||ADA & ICC A117.1
ASME A112.19.3/CSA B45.4
Buy American Act
CAN/CSA C22.2 No. 120
NSF 372 (lead free)
Having a problem with intermittent operation. My customer says sometimes the push button or sensor on bottle filler doesn't work. I have not witnessed this myself yet though. Any condition other than no water cause this?
Thank you for your question on the Elkay LVRCGRN8WSK EZH2O Bottle Filling Station & Single High Efficiency Vandal-Resistant Cooler. This could be flash freezing of the unit. One troubleshooting step you could try is to unplug the unit the next time the water stops flowing. After 30 minutes or so, if the water starts flowing, it is most likely freezing up. You could also check the cold control to see if it has been adjusted from the factory setting. The cold control is factory set to the middle of the adjustment range. You can also contact our Tech Services and they will be happy to help. They can be reached at: 800-260-6640 and select Option 3. Please call while you are at the unit in question as our Tech Services representative may have questions in order to help you properly.
Date published: 2021-01-15
Can I use a WSP 35000 filter in this equipment?
Thank you for your question on the LVRCGRN8WSK. Our WSP35000 from our International portfolio can be used with most Elkay products including the LVRCGRN8WSK. It will need to be installed before the product, as it will not fit inside of the unit the way our domestic filters do.
Date published: 2020-09-18
Can the right side be high and the left lower
No. This model is not available with right side high and left lower. It is also not field convertible. I called and spoke with Customer Care and was instructed to use VRCTLRWSK which does not have green compressor and bottle fill is push button rather than infrared. I don't know why Elkay can't just answer a question here on their own site instead of making you call in and waste 30 minutes on the phone. Irritating.
Date published: 2020-05-15
can this be used without the water filter?
Hello Dhutson918 - This is a non-filtered unit. If you have any other questions, please contact our customer care team for assistance. They can be reached at Phone: 800-476-4106 or Email: CustCare@Elkay.com. Thank you for your question!
Date published: 2020-03-16
Does this unit need one 120v feed or two. The rough in drawing shows two but only one marked as preferred.
Hello Ron B - This unit will need two feeds. Please reach out to customer care with any questions. They can be reached at Phone: 800-476-4106 or Email: CustCare@Elkay.com. Thank you for your question!
Date published: 2020-02-12
The number in the LED monitor show what? Number of bottles of 20 oz?
Hello! Our Green Ticker informs the user of the number of 20 oz. plastic water bottles saved from waste. Thank you for your question!
Date published: 2020-02-05
can this chilled water fountain with bottle fill be installed outside on a semi protected wall for summer use at a pool, it will be disconnected and stored inside during winter. Covered roof but blowing rain will hit it.
Hello Pool Guy - We would love to help you with this! Please reach out to our customer care team for assistance. They can be reached at Phone: 800-476-4106 or Email: CustCare@Elkay.com. Thank you for your question!
Date published: 2020-01-08
What makes these 'vandal-resistant'? Can someone explain that?
Hello my name is Alex and my work just but a this drinking Fountain the instruction for plumbing the lines to me are not clear so more help on what pipe hooks to what would be of great help. Also we changed it because the old one would not get cold any idea why that could have happened maybe some common problems you know of would help.
Date published: 2020-04-27